One of the most common misunderstood aspects of applying variable frequency drives (VFD) happens when you retrofit a motor with a drive for the first time. Often the VFD purchased is too small. This happens when a person says, “I have a 10 hp motor so I need a 10 hp drive.”
The problem is that when you start a motor across the line, it has unlimited current from the starter powering it—this current creates the high torque needed to start the motor with its associated load.
A VFD can only supply a limited amount of current. Current equals torque, hence less current less torque. While you may be able to run your load with that 10 hp drive you cannot start it up with that same drive. Many drives can only supply 150% of what they are listed for.
This means you may have to purchase a 25 hp (or larger) VFD to start your 10 HP motor.
11 thoughts on “Sizing Variable Frequency Drives”
BION I’m impressed! Cool post!
What a joy to find someone else who thinks this way.
Dude, right on there brother.
An answer from an expert! Thanks for contributing.
Your thinking matches mine – great minds think alike!
Action requires knowledge, and now I can act!
Glad to read this blog! Keep it going!
Hey, really like the blog, wordpress?
Yes, you are correct. Thanks.
We’re a bunch of volunteers and starting a new scheme in our community. Your web site offered us with useful info to work on. You have done an impressive job and our whole community might be grateful to you.
I think this is one of the most important information for me. And i am glad reading your article. But want to remark on some general things, The web site style is great, the articles is really excellent : D. Good job, cheers
Comments are closed.